Uniweld FV600 Oxy/Fuel Adapter is a fuel valve adapter that is used to connect a Uniweld acetylene MC regulator (CGA200) to a disposable fuel cylinder (CGA600). All Uniweld acetylene regulator diaphragms and seals are compatible for use with either propylene (MAP//Pro) or propane fuel gas.
Warning: Fuel compatibility with other manufacturer's acetylene regulators must be determined prior to use. If not compatible, another option would be to replace the Acetylene regulator with an RP3A regulator.
The Uniweld 71 welding handle and Type17 weld/braze tips will work properly using either of the fuel gases combined with oxygen. The CA550 cutting attachment will also work with wither fuel gas. However, the cutting tip is fuel specific and must be changed. Also, Uniweld's Cap'n Hook tips are fuel specific. It is recommended to use grade "T" hose (part# H32AT) with propylene (MAP//Pro) or propane fuel gas. If using grade "R" hose (part# H32A) with propylene (MAP//Pro) or propane fuel gas, it must never be used in extremely cold temperatures below -10 °F. This may cause the fuel gas to liquefy and act as a solvent that will attack the internal hose material. Always bleed off the remaining fuel gas in the hose after each use.
NOTE: There will be a noticeable performance and temperature difference when using propylene (MAP//Pro) versus acetylene and an increase in oxygen consumption. Acetylene burns at 5589 °F with an oxy/fuel ratio of 1-1 respectively. MAP//Pro burns at 5193 °F with an oxy/fuel ratio of 3.5 - 1. Propane burns at 4579 °F with an oxy/fuel ratio of 4 - 1. It is highly recommended to use a Type17-3 or larger tip for brazing 3/8" and 7/8" copper line sets.
|Name||Uniweld FV600 - Oxy/Fuel Valve Adaptor To Connect a CGA600 To CGA200|
|Gemaire Item Number||FV600|
|Manufacturer Product Number||FV600|
|SKU - PIM Number||1422394408182|
|Unit of Measure||EA|
|EPA Cert Required||No|
|Country of Origin||USA|
|Warranty Offered||1 Year|
|GEM - Case Quantity|